Float and Thermostatic Traps
Automatic and continuous elimination of condensate and air at steam temperature increases system efficiency.
Float and thermostatic traps operate on the density principle. A thermostatic vent in the top of the trap allows free passage of air during start-up, and closes near saturation temperature. Condensate fills a float chamber, causing a float to rise, and through a lever mechanism pulls a valve off its seat and opens the orifice of a discharge valve. The opening and closing of the seat provides modulation to handle light or heavy condensate loads.
The discharge valve is under condensate water. The water forms a seal that prevents live steam loss. This also prevents the venting of air and non-condensable gases. The accumulation of air and non-condensable gases causes a significant temperature drop. The thermostatic valve in the top of the trap discharges these gases.
Operation of Float & Thermostatic Traps:
During start-up, the thermostatic vent is open to allow free passage of air.
A lever connects a ball float to a valve and seat. When the condensate that fills the float chamber reaches a certain level, the float rises pulling the valve off the seat, opening the orifice of the discharge valve and draining the condensate.
The thermostatic vent will close near saturation temperature. The balanced design allows venting of non-condensables that collect in the float chamber, when operating at design pressure.
The condensate port is normally closed during no load. As condensate enters the float chamber, the float and lever mechanism movement opens and closes the seat to provide drainage equal to the condensing rate.
Characteristics of Float & Thermostatic Traps:
Primary Applications of Float & Thermostatic Traps:
Features and Benefits
General Selection Tools:
Heat Exchanger Product Selection
Steam + Water Pressure Reducing Values
Report Bugs/Request Enhancements
Please email the following address to report issues and request enhancements: email@example.com
Consult your local Bell & Gossett Representative for additional assistance.
Search below to find your local distributor. If there is no location found, please contact our regional office for more information.